Fire extinguisher inspection has a lot to do with the safety of employees in the workplace. A positive inspection result gives a positive security to the business. By using a fire extinguishers Australian standards checklist, it is effortless to accomplish complete fire safety coverage. Start by getting to know the importance and different procedures in inspections.
Why does your workplace need fire extinguisher inspections?
Inspections are primarily done to keep track on the condition and performance of your fire extinguishers. The process determines if the installations are properly mounted if there are signs of malfunction, if they show clear signs of replacement and whatnot. Professional electricians are hired to determine these dangers and fix them to prepare your workplace for fire incidents.
These fire safety inspections are necessary to determine underlying issues that may cause hazards, and electricians may recommend corrective action and control the possible risks of fire. Therefore, conducting a cohesive and regular inspection is a significant part of the fire extinguisher inspection requirements and management system.
Fire extinguisher inspection
As simple as a fire extinguisher, one might not recognize the nitty-gritty details of inspecting this equipment. Have a short review on these fire safety guidelines to familiarise the necessary maintenance processes.
A tank will need hydrostatic testing when it shows signs of corrosion and mechanical injury. This type of process will test the strength and weakness of the vessel in order to stabilise the pressure needed when the tank is in function. Hydrostatic testing must be performed by a trained fire electrician after performing an internal examination of the shells and cylinders.
Make sure you have the right type of extinguisher
Each extinguisher is matched with the potential fire that might occur in the workplace. Extinguishers are labeled according to the class of fire they are capable of suppressing. The inspection is necessary to see whether the fire extinguisher supply suits the possible fires in the premises, especially with a changing environment.
Checking the accessibility of a fire extinguisher is ensuring they are located in the right spots and installed at the required minimum and maximum meters between the floor and the extinguisher. The ideal measurement is at least 100mm between the base of the unit and the floor and a maximum of 1200mm between the top of the unit and the floor. Make sure a person with an average height, which is 5’6”, can reach it. Furthermore, an accessible extinguisher is visibly located near emergency exits and is free from obstruction that may cause delay or inability to get it.
The ideal measurement is at least 100mm between the base of the unit and the floor and a maximum of 1200mm between the top of the unit and the floor. Make sure a person with an average height, which is 5’6”, can reach it. Furthermore, an accessible extinguisher is visibly located near emergency exits and is free from obstruction that may cause delay or inability to get it.
Secure the locking pin
The small pin used to lock the handles is essential in securing the extinguisher from releasing its contents accidentally. The pin is locked in the lever by tying a plastic fastener into the circle of the pin and the lever together. This prevents the pin from being pulled out by unauthorized persons or accidentally loosening.
Check the hose condition
The connection between the hose and the shell can acquire natural wear and tear such as cracks, leakage, and thin spots. These signs of deterioration can affect the performance of the extinguisher. Aside from the passageway of the tank’s contents, the nozzle, which is the mouthpiece of the equipment, might endure obstruction such as paper, gum and tiny objects. This will cause pressure build-up and will block the contents from discharging.
Attach an inspection record to the extinguisher
An inspection record indicates the date of inspection, findings, and course of action taken. This is attached to the extinguisher to serve as a reference for future inspections.
Things to note
Fire extinguishers should be inspected every 6 months. For portable extinguishers, they require replacement when it has been used. On the other hand, regular fire extinguishers may only require refilling once it has been used.
Looking to conduct fire extinguisher testing in your workplace? Know your fire protection technician.